Jarrod, thanks for your hospitality Saturday.
I have a disclosure to make. I did not connect a protective ground wire to the two outlets I installed, because I did not find a protective ground coming from the panel board. The devices will be grounded as long as the conduit stays intact. Unfortunately, fittings tend to come loose over time.
I thought the conductors I used might have been too big, and the conduits and boxes might have been too small. Looking at the NEC today confirms my suspicions. I created a page of data from the NEC. As you can see, a 1/2" EMT conduit has room for only one 6 AWG THHN conductor. A 4" junction box does not have room for any 6 AWG conductors at all.
I like the larger than required conductors, because they stay cool, but they also need larger conduits and boxes.
I also found out today that wire nuts go up to 8 AWG maximum.